Modified on: Tue, 25 Jun, 2019 at 5:44 PM
The Honeywell Lyric Controller has the ability to detect loss of power. An AC LOSS occurs when the primary input voltage drops below 9VDC. AC Loss will be displayed on the screen. After approximately 1 minute of Power Loss and no keypad activity, assuming the backup battery is good, the entire Touch Screen will go dark in order to conserve the battery regardless of programming.
Press the touchscreen to bring the display back up. Again, after about 30 seconds of no activity, the display will go dark. If power restores while the screen is blanked out, it will come back up, and the AC Loss display clears automatically.
An AC LOSS Report will be randomized up to a 4-hour delay. If AC power is restored before the AC Loss report is sent, there will be no AC Restore report. The Maximum distance between the Power Supply and the Lyric Controller is 8ft with 22 gauge wire, 13ft with 20 gauge and 22ft with 18 gauge 2 conductor wire.
If you are looking to reduce your monthly alarm monitoring rates for your home or business make sure to contact AlarmClub at 1-844-335-5897 for your free consultation! *We are usually able to takeover just about any kind of security system so don’t hesitate.
Alarm Monitoring Services
Honeywell Lyric Controller FAQ’s
Honeywell Lyric Controller Manuals
All Honeywell Lyric Security System Video's Playlist :
Did you find it helpful?Send feedback
Sorry we couldn't be helpful. Help us improve this article with your feedback.
Do You Have any Discussion Comments?
comments powered by Disqus